As a minimum, all plastic heating oil tanks should be installed on a flat, level, fire resistant surface, capable of supporting the weight of the tank when fully laden. Where concrete slabs are used, they should be at least 50mm thick.
The base should extend at least 300mm beyond the widest points of the oil tank and fully support the base of the oil tank in its entirety. Piers are not suitable for this purpose and will cause irreparable damage to the oil tank, resulting in premature failure and catastrophic product loss.
Detailed oil tank base requirements can be found within OFTEC Technical Instruction Book 3.
With our Harlequin ITE range of oil tanks, there are three types of gauges within the tank pack:
Apollo Visual Tank Pack
Includes an Apollo Visual oil tank contents gauge which comprises of a tank mounted transmitter unit and plug in receiver unit, along with a bottom outlet kit. Apollo Visual as well as reporting the fuel level to a plug in receiver also has a built in LCD display on the transmitter incorporating an on tank level.
Includes an Apollo Smart oil tank contents gauge which comprises of a tank mounted transmitter unit and plug in receiver unit, along with a bottom outlet kit. Apollo Smart Receiver Unit benefits from a mains power supply, and simply plugs into a standard socket, allowing you to monitor oil heating usage from almost any room in your home or office.
*請注意 - Harlequin HQI係列不包括罐裝包裝。